CJ1W PRM21 PDF
CJ1W-PRM21 Omron Automation and Safety Controllers CJ1 Profibus Master datasheet, inventory, & pricing. This article (NJ base) explains how to setup the configuration for the NJ with a CJ1W-PRM21 Profibus communication unit connecting. Buy Omron CJ1W Series PLC I/O Module, 31 x 90 x 68 mm CJ1W-PRM Browse our latest plc-i-o-modules offers. Free Next Day Delivery.
|Published (Last):||26 June 2006|
|PDF File Size:||4.72 Mb|
|ePub File Size:||14.65 Mb|
|Price:||Free* [*Free Regsitration Required]|
Hello, the BF led blink in the omron master, the slave appear only with the led run. Hope this helps, Daniel Chartier.
myOMRON Europe: Services & Support
Sign In Sign Up. Started by malyalewariat18 March. You need to be a member in order to leave a comment.
When i try to use scan option i get another error:. But it’s possible that the problem is the hardware config. This contribution was helpful to 1 thankful Users dchartier. I configured in S7 project the slave parameters. I should do any thing else, Thaks. Site Explorer Site Explorer. ci1w
Hello Ariel; In your diagnostic messages a few stand out, at first glance ArielP 10!! Seeing the scan returns error with DTM version 1. The master tell me that the slave have a invalid response. I don’t have this software installed on pc The number of bytes its going to recive and send. When i try to use scan option i get another error: In the front of the module apeare that is the version 2.
Share this post Link to post Share on other sites. Sign up for a new account in our community. I uploaded the file already. Following DTM reported the error: So many communication protocols to choose. If this is already done, it would be good to see how they have been configured. The module was update to firmware V3, but I have only in step 7 the product versions 1 and 2.
I can now use diagnostic option and I can see states of plc and module. I made a diagnostic to de cp and appear this error: Try to run the AutoUpdate so you’ll get a newer version if you have a registered copy.
Product Support Services Forum mySupport. Follow us on Twitter Youtube. What about those errors? I’ve set up correct connection parameters of pr2m1 profibus master.
Am I missing CX-Server? I also programed the functions send and recv acording with the master configuration. Edited 21 March by malyalewariat. Hello Ariel; You seem to have had difficulty in uploading your ch1w information.
Here I have que diagnostic of the cp slave. I was sure that I’ve tried all but I didn’t.
I’m almost sure that this bosch unit provides profibus connection. It supposed to be toolbus usb in configuration tab, and now i can use test, and go online cm1w without any errors.
Started by malyalewariat18 March prm21 cj1w bus profibus. Posted 21 March edited. All about Decentral Peripherie.
The GSD file you will find here: