CAN ULC S536 PDF
CAN/ULC-S PERIODIC INSPECTIONS AND TEST – DAILY AND MONTHLY. NOTE: Refer to Appendix D for examples of Inspection and Test Record. SCOPE. This Standard provides requirements for the inspection and testing of fire alarm systems and specifies the devices and functions to be inspected. 1 SCOPE This Standard prescribes requirements for the inspection and testing of fire alarm systems and specifies the devices and functions.
|Genre:||Health and Food|
|Published (Last):||9 August 2012|
|PDF File Size:||18.83 Mb|
|ePub File Size:||18.88 Mb|
|Price:||Free* [*Free Regsitration Required]|
Alarm devices inspected to verify they are free from physical damage? Hose rack assembly pressure reducing valve partial flow test.
CAN/ULC-S536-04 Fire Alarm Annual Inspection Test Form
Detector tubes must be pulled and their alignment confirmed if results indicate any abnormalities. This document has been provided to the building owner or their authorized representative who has acknowledged receipt of same below.
Is the building occupied? T Generator provides power to the AC circuit serving the ylc alarm system. Test batteries for specific gravity and state of charge? Confirmation of wiring supervision and ground fault indication is required to be carried out at all end-of-line devices on an annual basis.
These units are vulnerable to electrical cam they won’t function in the absence of power. Refer to Appendix F1 ; P iii Silent accelerated test.
A B C Confirm that a trouble signal e536 received at the control unit or transponder under an open loop fault. Interior of dry-pipepre-action, deluge valves internal inspection? Displays are visible in the installed location. Check the date stamp located on s53 back of the detector and ensure you follow the care hlc maintenance instructions that came with it to make sure to keep it operating at peak efficiency. Testing Items Quarterly Water flow alarms passed test and provide correct annunciation?
The montly test is to ensure that all audible and visual alarm indicators function properly and are loud or visible enough to alert all the occupants to a fire condition.
Interior of dry pipe valve cleaned? Description Type Model No. Gauges wet pipe in good condition and normal water pressure is being maintained? Check heat trace controller for trouble and ground fault response.
Smoke detector alarm verification status change confirmation verified. Yes No Oil Pressure: There is reason to believe the system contains sodium silicate? Smoke and fire detectors should be considered an integral part of any home or business security system. Fire Safety and Emergency Planning. Where active and supporting field devices are utilized, device labels correspond with actual field location.
Was water delivered to inspectors test connection? Ground fault tested on positive and negative initiates trouble signal. Reconnect ancillary functions off site connections? The communicator has been reset following completion of testing. If the sensor is part of an actual fire alarm system, make sure you alert other tenants in the building as to what you’re doing as well as your monitoring station if applicable.
Cabinets accessible and identified? The communicator is trouble free. The printed maintenance and testing guide must be followed. Forward flow test has been conducted.
Fire Alarm System Periodic Inspection (CAN/ULC-S)
Identify conventional field device locations. Plugging of sprinklers found during activation or alteration? Audibility of alarm sounder checked? Recommended Additional Testing not mandated by the Standard: Confirm field device free of foreign substance.
Dry-pipe full flow trip test to be done every 3rd year: P Emergency telephone operable or in-use tone at handset operates.
Main Power supply failure trouble signal operates. Check heat trace controller interconnection to fire alarm system.
Alarm valves shall be inspected externally. Record anti-freeze Specific Gravity: The common control employs several features to enable the occupants to identify any specific problems within the system.
Circuits for emergency telephone trouble operation, including visual N indication, operates. A security or fire alarm system that employs integrated smoke detectors is by far the best way to protect your family or workers. Test exhaust for excessive back pressure? There are a total of: Gauges checked against calibrated gauge or replaced? Reducer and cap are not missing?
Hose properly racked or rolled?